Add Compatibility to a strange 30RQ chiller.
Remove feature introduced by 2.2 (Release forced point when initialization).
Buffer overflow while convert Unicode string to utf8.
WebUI use basic authorization method.
WebUI table index overflow (Thanks to Nitin)
WebUi show Ethernet address.
Discard character out of 0-9, a-z, A-Z in string.
Selectable 0.001，0.01，0.1，10，100，1000 multiply mapping
BACnet version merge bugfixs from BACnet Router firmware.
Low level api changed, prepare for future product
Bug introduced in 2.1 is fixed: continuous error after communication fail.
When initialize device, if point is forced by high priority, release it.
Firmware filename has version and crc.
Show version on left tree menu.
Auto refresh page after reboot or firmware upgrade .
Other ui bugfixs.
Some of customers want to access real time and internal detailed parameter stored in maintenance table.
Now new released CCN Gateway firmware support maintenance table. If you have CCN Gateway and want a upgrade, please contact us.
CCN Gateway for BACnet support BACnet IP, BACnet Ethernet, BACnet MSTP. If you want it work as a router, you should enable more than one BACnet interface, and configure network number. As below:
For user to get familar with CCN Gateway, we build up simulated DEMO Gateway.
This demo Gateway link with 6 CCN chillers, each has same bus number of 0, element addreses are from 1 to 6.
The username to acces is: admin, no passowrd is needed.
For modbus gateway, the acces point is http://demo1.hvacrcontrol.com
For BACnet gateway, the access point is http://demo2.hvacrcontrol.com
User could use modscan or VTS to test the modbus/BACnet function. The port number is defined in the Gateway’s general setting section.
Because the accsss is open, if there are users operate it concurrently. it would behave strangely. If you want exclusively operate it, please contact us, we would give you other private access point.